- PRODUCT HIGHLIGHTS
- HOW TO APPLY
• Low peak exotherm • Low dusting, ready-to-mix, pre-portioned kits • Moisture tolerant • Corrosion and impact resistant • Stress and chemical resistant • High compressive, tensile and shear strengths • High vibration resistance
• Do not thin with solvents. Solvents will prevent proper cure • Minimum grout thickness: 1 in. (25 mm) • Maximum grout thickness: 18 in. (450 mm) per lift. For grout thickness between 12-18 in • Grouting material must be stored in an area with ambient temperature between 73° and 86°F (23° and 30°C) for a minimum of 48 hours before use • Cold ambient, substrate or material temperatures will inhibit the flow and curing characteristics of Sikadur 42 Grout-Pak LEUS. For temperatures below 73.4°F (23°C)
Pour the mixed grout into the prepared forms from one or two adjacent sides only, to eliminate air entrapment. Maintain the liquid head to ensure intimate contact to the base plate. Place sufficient epoxy grout in the forms to rise slightly above the underside [3 mm (1/8 in)] of the base plate. The minimum void depth beneath the base-plate should be 25 mm (1 in), but 38 mm (1.5 in) is preferred. Where the void beneath the base plate is greater than 450 mm (18 in), place the epoxy grout in successive 450 mm (18 in) lifts or less, once the preceding lift has cooled.